Ask an Expert: DCS System Log and Quantum I/O Network Errors
PUBLISHED ON Jul 06, 2010
by Milt Beebe, Preventative Maintenance Expert
Q: Does your DCS system log show Quantum I/O network errors? How do you know if your Quantum (S908) network is working correctly?
A: S908 network cables and taps, as any other physical network, are subject to the environmental hazards which may be present: animals, sunlight, water, corrosives, extreme high and low temperatures. NovaTech Automation recommends the health and condition should be certified at installation and routinely checked (3- 5 years) with a high-resolution MTDR (Metallic Time Domain Reflectometer).
Hand held testers used for Ethernet testing do not do a good job testing S908 cabling systems, despite the fact that most of them have BNC connectors and claim they are good for coaxial cable testing. Each copper segment must be tested. Testing several copper segments connected by taps, splices, or couplers does not yield meaningful results.
S908 segment analysis can find, document, and restore a network segment such as shown in the above “before” and “after” TDR charts.
In addition, the network check should include a physical check of each drop cable, trunk cable, and tap to ensure the cables are properly supported, and do not exceed minimum bend radius (20 times the cable diameter).
Got a Preventative Maintenance or Reliability-Centered System Life Planning question we can clear up? Email Milt.Beebe@novatechweb.com
May 15, 2010
Congressman Charlie Dent Visited Bitronics to raise a flag for a 100% Made in America product
Congressman Charlie Dent Visited Bitronics today to raise flag for a 100% Made in America product. Rep. Dent to inspect production process and present a flag that had been flown over the U.S. Capitol to commemorate Bitronics® 100th year of...
Mar 30, 2010
What's a 2 1/2 Element Configuration?
Q: I have 2 PTs and 3 CTs available to connect to your wattmeter. Is that called a 2½ element configuration? A: In the context of measuring three-phase power, it all depends on whether your PTs are connected line-line or line-neutral....
Mar 30, 2010
50 Series and 70 Series Families Meet NERC BAL-005-0.1b
The revised (May 2009) NERC BAL-005-0.1b standard states, “Each Balancing Authority shall at least annually check and calibrate its time error and frequency devices against a common reference. The Balancing Authority shall adhere to the minimum...